Aluminum Core PVC Insulated Electrical Power Cable
50000 Kilometer/Kilometers per Month
Packaging & Delivery
Export standard wooden drum or as you request
Qingdao or Shanghai port
*Type of Service Drop Cable:
Duplex Service Drop
Triplex Service Drop Quadruplex Service Drop
Concentic strand or cmpressed 1350-H19 conductor, polyethylene or cross linked polyethylene insulation, concentric strand AAC, ACSR, or 6201 alloy nertral messenger.
The cable can be produced whose construction is phase conductor with neutral bare conductor or phase conductor with insulated neutral conductor, etc. And we can still produce the cables according to the request of customers.
*Triplex Service Drop
To supply power from the ulility`s lines to the consumer`s weatherhead. For service at 600 volts or less(phase to phase ) at a conductor temperature of 75 maximum for PE insulation or 90 maximum for XLPE insulation.
*Quadruplex Service Drop
Used to supply 3 phase power, usually from a pole-mounted transformer to the use`s servic head where connection to the service entance cable is made. To be used at voltages of 600 volts or less phase to phase and at conductor temperature not to exceed 75 for PE insulated conductors or 90 for XLPE insulated conductors.
1. B-230 Aluminum Wire, 1350-H19 for Electrical Purposes. 2. B-231 Aluminum Conductors, Concentric-Lay-Stranded. 3. B-232 Aluminum Conductors, Concentric-Lay-Stranded, Coated Steel Reinforced (ACSR). 4. B-399 Concentric-Lay_Stranded 6201-T81 Aluminum Alloy Conductors. 5. B498 Zinc-Coated Steel Core Wire for Aluminum Conductors, Steel Reinforced (ACSR). 6. Duplex Service Drop cable meets or exceeds all applicable requirements of ANSI/ICEA S-76-474
If you have any problems and need,pls contact us : sales002(at)aobest.cn
Triplex Service Drop
Construction : 2*(AAC conductor +PVC insulation)*AAC Conductor
Quadruplex Service Drop
Construction : 3*(AAC conductor +PVC insulation)*AAC Conductor