PVC Sheathed XLPE Insulated High Voltage Power Cable
1.ISO 9001:2000, CCC certificate
2.Qualified produts at competitive price.
Introduction: The products can be produced according to our factory specification which is equivalent to the standard IEC60502. The factory can also design and manufacture special XLPE cable according to the other standards required by the customers. They not only have excellent electric, mechanical properties, but also have powerful resistance against chemical corrosion, heataging and environmental stress. Their structures are simple. The permissible maximum operating temperature is 90C. It is convenient for using, and they can be laid with no restriction of different elevation.
The Rated Voltage(kv):
1st class 0.6/1 1.8/3 3.6/6 6/10 8.7/15 12/20 18/30 21/35 2nd class 1/1 3/3 6/6 8.7/10 12/15 18/20 - 26/35
No of Core and Range of sectional Area (mm2) 1 Core 1.5-800 25-800 25-1200 25-1200 35-1200 50-1200 50-1200 50-1200 2 Core 1.5-185 25-185 3 Core 1.5-400 25-400 25-400 25-400 35-400 50-400 50-400 50-400 4 Core 2.5-400 25-400 5 Core 2.5-400 25-400
Cu Core Al Core The Type and Main Application (1)YJY YJLV XLPE insulated, PVC or PE Sheathed Power Cable For laying indoor, tunnel, channel and undergroud, Unable to bear external mechanical force, but bear the traction force during laid (2)YJV22 YJLV22 XLPE Insulated, Steel Tape Armoured, PVC or PE Sheathed Power Cable For laying indoor, tunnel, channel and undergroud Able to bear external mechanical force, but unable to bear large pulling force (3)YJV32 YJLV32 XLPE Insulated, Fine Steel Wire Armoured, PVC or PE Sheathed Power Cable For laying in shaft with large difference of level. Able to bear external machanical force and maderate pulling force (4)YJV42 YJLV42 XLPE Insulated, Thick Steel Wire Armoured, PVC or PE Sheathed Power Cable Able to bear positive pressure and pulling force
"ZR-"Include ABC three kinds of flame retardent cables, which are spectively indicated in "ZRA-" or "ZRB-" "ZRC-". For example: "ZRB-YJV""ZRA-YJV22".
Main Technical Quota 1. DC resistance: Conductor resistance of finished cable at 20Cper kilometer is not more than the following values.